A new consumer unit will offer much greater levels of protection compared to an older model or an outdated fusebox.
Flameport Electrical can install a new consumer unit, including a full test and inspection of the entire installation, ensuring that it is safe and suitable for continued use.
Replacing a consumer unit is not just remove the old and install the new. An existing installation must be fully tested and inspected to ensure it is safe for continued use, and it's very likely that some minor repairs will be required.
Typically, it will involve:
In almost all installations, this is at least a full days work, and can easily be more for larger installations or those that require more extensive repair.
Beware companies and individuals that offer such things done in just a few hours - they may be cheap, but you are only getting a small part of what needs to be done.
Unfortunately there are many installations which haven't been inspected in decades, and that assumes it was all done properly in the first place.
Subsequent alterations and additions may have been done correctly - or perhaps not.
An RCD is a device which continuously monitors the current flow in the line and neutral conductors, and disconnects the supply if any difference is detected. This could be due to a cable being damaged, a faulty appliance or someone touching a live part.
RCDs are designed to protect people and save lives - disconnecting the power if more than 30mA (0.03 amps) flows somewhere other than the circuit wiring.
Fuses and circuit breakers are there to prevent the cables from overheating. They will not disconnect if someone touches a live wire.
Many older consumer units have a single RCD that covers some circuits only. Some do not have RCDs at all, including older installations with cartridge fuses or rewireable fuses.
A few have a single RCD that covers all of the circuits - but this means that any fault results in the entire house being disconnected, and remaining that way until the fault is removed.
Favoured by many, dual RCD consumer units have two RCDs, with the installation split into two parts. A fault that causes one RCD to trip will disconnect about half of the circuits, leaving the rest operational.
While this is better than having everything disconnected, it is still very inconvenient. A faulty toaster could result in the lighting upstairs being disconnected, or a defective electric shower might result in the supply to your home office being cut off.
An RCBO is a single device that contains both an MCB (circuit breaker) and an RCD. With these, any fault only disconnects one circuit - others are unaffected.
RCBO consumer units do cost more than the dual RCD types, but for smaller installations the difference is insignificant.
Larger installations typically with 10 or more circuits will be cost significantly more - but in reality a dual RCD consumer unit isn't appropriate for those anyway, as once again a single fault will result in large numbers of circuits being disconnected.
Surge protection can be included in the consumer unit to protect equipment in the installation from high voltage transients or spikes.
Voltage transients can damage electronic equipment, which in a modern home is almost everything - even traditionally basic appliances such as cookers, washing machines and fridges now contain electronic devices.
Properties with overhead supply cables and/or those in areas with high levels of lightning strikes each year are particularly vulnerable. However properties with underground supplies are certainly not immune, and some high voltage transients are caused by other electrical equipment being switched on or off, both within the installation and in nearby ones.
Adding surge protection at the time of replacing a consumer unit will typically cost around £100 extra - but that's a fraction of the cost of replacing a damaged television, laptop or game console.
Arc Fault Detection Devices, or AFDDs are a relatively new protection device. They continuously monitor and analyse the current flowing in a circuit and will disconnect power if arcing is detected.
For a free, no-obligation quote to replace your old fusebox or consumer unit, please contact me.